Skuttle 120V 13 GAL High Capacity Steam Humidifiers Model F60-1 with Automatic Flushing Timer.
Skuttle Duct-Mounted Steam Humidifiers are the best option when stabilized humidity is desired or essential. They work well on all heating systems with air movers, and are particularly effective on furnaces that don't operate long enough or generate enough heat for other humidifiers to work efficiently. Skuttle has been the leader in residential steam humidification for more than 20 years.
How Steam Humidifiers Work
Inside a Skuttle Steam Humidifier, a water temperature sensing device operates the furnace fan independently from your home's heating system. Because it has its own heat source, a steam unit will effectively humidify your home regardless of the air temperature.
Standard Models 60-1 and 60-2 come equipped with Compustat-an electronic, temperature-sensing humidistat that adjusts automatically to weather changes. Models F60-1 and F60-2 are identical to the standard units, except that they include a Skuttle Automatic Flushing Timer and Chlorine Removal Filter to minimize maintenance.
Rather than being duct-mounted, Model 60-BC1 is a free-standing unit. It's an ideal choice when no ductwork is available, or when using the central air distribution system is not an option.
Skuttle Steam Humidifiers are efficient because they use comparatively little water. However, since they operate independently from your heating system, they use a significant amount of electricity. Steam Humidifiers do not produce harmful contaminants, nor do they release them into the air.
Due to Steam Humidifiers' internal complexity and the danger of scalding, cleaning and servicing by a qualified HVAC contractor is strongly recommended. The normal service interval varies from one-to-three months (i.e., one or two cleanings during a typical humidification season, plus a thorough cleaning at the end of the season). Water hardness, weather conditions, home construction, etc., all affect cleaning frequency. Use of a Skuttle Automatic Flushing Timer can reduce maintenance significantly.
The humidifier and the connecting water valve must be turned OFF at the end of each heating season.
|60-1 Moisture Output Capacity|
|Pounds per Hour||4.5|
|Gallons per Hour||0.54|
|Gallons per Day (GPD)||13.0|
|Duct Opening||10-1/2" x 8"|
|Heating Element Specifications|
|60-1 Internal Heat Source||1.5 kw, 120V, 12.5 amps incoloy sheathed element|
|60-2 Internal Heat Source||2.0 kw, 240V, 8.3 amps incoloy sheathed element|
|Home/Humidifier Sizing Chart|
|Tight House||Average House||Loose House|
|3,095 sq. ft.
|1,970 sq. ft.
|1,413 sq. ft
|4,048 sq. ft.
|2,576 sq. ft.
|1,848 sq. ft.
|Tight House||Insulated walls and ceilings; vapor barriers; weather stripping on doors and windows; snug doors, windows and fireplace damper. One-half air change per hour.|
|Average House||Insulated walls and ceilings; vapor barriers; loose doors, windows and fireplace damper. One air change per hour.|
|Loose House||No insulation, storm doors, storm windows, weather stripping or vapor barriers. Two air changes per hour.|