Roll over image to zoom in
Control line voltage valves of a fan coil unit in cooling, manual or automatic changeover heating-cooling systems.
- Directly operate one or two valves
- Positive deadband separates heating and cooling circuits in automatic models
- Includes allen wrench for cover and mounting screws
|Description||120 to 277 Vac 4 pipe Fan Coil, manual heating-cooling|
|Application||4 pipe fan coil, manual heat-cool changeover|
|Switch Positions (System)||HEAT-OFF-COOL|
|Switch Positions (Fan)||HI-MED-LO|
|Setting Temperature Range (F)||55 F to 95 F, marked COOL-WARM|
|Setting Temperature Range (C)||13 C to 35 C, marked COOL-WARM|
|Voltage||120 to 277 Vac|
|Electrical Ratings||Fan Switch: 120 Vac: 5.5 AFL, 33.0 ALR; 240 Vac: 2.75 AFL,|
16.5 ALR; 277 Vac: 2.4 AFL, 14.4 ALR
|Electrical Ratings||Thermostat (Valve load): 120 Vac: 0.32 AFL, 1.0 A ALR; |
240 Vac: 0.16 AFL, 0.50 ALR; 277 Vac: 0.14 AFL, 0.43 ALR
|Differential Temperature (F)||The differential from make of one|
contact to make of the opposite contact is 7 F maximum with a positive deadspot.
|Differential Temperature (C)||The differential from make|
of one contact to make of the opposite contact is 4 C maximum with a positive deadspot.
|Mounting||4 in. square outlet box or 2-ganged outlet box|
|Dimensions (in.)||4 5/8 in. high x 4 15/16 in. wide x 1 5/16 in. deep.|
|Dimensions (mm)||118 mm high x 125 mm wide x 33 mm deep|
|Operating Humidity Range (% RH)||5 to 95% RH, non-condensing|
|Approvals, Underwriters Laboratories Inc||File No. E34436,|
Vol 2, dated 3-19-73; Guide No. XAPX
|Approvals, Canadian Standards Association||Certified|
|Includes||Allen wrench for cover and mounting screws|
Payment & Security
Your payment information is processed securely. We do not store credit card details nor have access to your credit card information.