Same as MEP100. Force 5 minute purge delay after main flame fail.
The Fireye MEP100, MEP100P, MEP101, MEP102, MEP103, MEP104, MEP105, MEP106 MEP107, MEP108, ME109, MEP130, MEP141 and MEP149 Programmer Modules are used with the Fireye Modular MicroM control. The operational characteristics of the control are determined by the selection of the programmer module (e.g. re-light, 2-stage capability, pilot cutoff, etc.). The programmer module incorporates a plug-in design for easy installation.
The advantages of the Micro M are zero dependence on discrete components previously used for timing functions. The MicroM, through the use of micro-controller technology, incorporates smart diagnostic LED’s, smart reset function for multi-burner applications, optional alpha-numeric display output (ED510) and serial communications via a Modbus-RTU.
Flame Failure Response Time (FFRT) is determined by the selection of the amplifier module. Test jacks are also provided on the flame amplifier module to permit flame signal measurement during operation. For proper and safe application of this product, you must refer to Fireye bulletin MC-5000 for a detailed description of the various programmer modules, including installation instructions, amplifier selection, operating sequences for each programmer module, etc.