The BAE165 US thermoelectric resettable tripping device operates in conjunction with a UL listed Belimo FSxx Series actuator for use in fire & smoke applications. The BAE drives a motorized fire damper to its safe position when the temperature at the damper (tripping temperature) exceeds 165°F. The device is connected in series with the power supply of the fire & smoke control actuator.
NOTE: The UL555(S) rating carried by the damper and the actuator is assigned as an assembly and can not be added in the field. The wiring method must be in accordance with Class 1 field wiring method as required by National Electrical Code (NEC_NFPA70). Use suitable UL or Canadian Certified wire. Jacket wires with suitable flexible conduit. Mount the flexible conduit into the BAE165 US metal bushing by means of the provided screw with a torque of 10.6 in-lb [1.2 Nm]. Properly terminate the conduit in a suitable junction box. Flexible conduit connection shall be grounded in order to maintain the proper basic insulation of the device.
|Rated voltage||24-240 VAC|
|Operating temperature thermal trip||165°F (74°C)|
|Protection class||grounded enclosure|
|Ambient temperature||-22 °F to 122 °F [-30 to 50 °C]|
|Storage temperature||-40 °F to 122 °F [-40 to 50 °C]|
|Housing||NEMA 1, enclosure type 1|
|Agency listing||cULus listed according to: UL 873 and CSA C22.2 NO. 24-93|
|Weight||0.88 lbs [0.4 kg]|